The Balance Tank is used to adjust the flow of water circulating in the system so that the system is not damaged during the transfer of the heated water in the boilers used to meet the heat need in the mechanical installation to the places with the necessary devices.
In addition, the water in the installation loses heat while returning to the boiler from the installation, the emergence of this temperature difference causes thermal stresses in the boiler and reduces the life of the boiler. One of the main tasks of the balance tank is to provide the thermal balance by mixing the cooled fluid coming from the installation with the hot water coming from the boiler.
There is no hydraulic interaction between the boiler circuit and the heating circuit.
Boilers and heating lines operate under the appropriate amount of water.
It can be used in single or multi-boiler systems, independent of the heating circuit control systems.
Adjustment elements on both sides of the balance tank work optimally.
Boiler circuit and adjustment elements are dimensioned more smoothly.
In order for the balance tank to work properly, the right choice must be made. According to the boiler capacity, the selection of the balance tank should be done well. If it is selected small, pressure drops occur and may even cause air formation, and may cause the boiler not to work properly. There must be a thermometer on the Balance Tank.
Balance tank connection types are in three ways. It is produced as screw connection up to certain diameters. In other diameters, it is produced as welded and flanged.
BALANCE TANK DIMENSIONS
AR-GE Group Boiler reserves the right to change values and tables without notice.
AR-GE GRUP KAZAN MAKİNA VE ISI SİSTEMLERİ İMALAT İTHALAT İHRACAT SANAYİ TAAHHÜT TİCARET LTD ŞTİ
Ostim O.S.B. Cevat Dündar Caddesi No:20
Yenimahalle - ANKARA
Telephone : 0 312 354 11 62 - 354 11 72
All rights of this site belong to AR-GE Grup Kazan Makina ve Isı Sistemleri Ltd Şti
Copyright © AR-GE 2020 All rights reserved